Important Cookie Information - this message will appear only once
Warm Water Total Server Cooling for Data Centers RackCDU ISAC™ sealed servers with In-Server Air Conditioning capture nearly 100% of server heat providing data center cooling cost reductions exceeding 50%. By capturing almost 100% of the heat from server racks, ISAC provides a key element for OEMs which need to provide thermally “room neutral” data centers as part of their offerings. ISAC also provides a method of providing reliable data center operations in extreme environments where pollutants, dust and dirt are a factor in overall air quality. As a sealed system, ISAC eliminates concerns with air quality.
Like RackCDU D2C™, ISAC includes direct-to-chip coolers for CPU, GPU and co-processor cooling. What makes ISAC unique is the inclusion of In-Server Air Conditioners which enable ISAC to cool the remaining components without exchanging air between servers and the data center.
RackCDU ISAC is deployed at a rack/server level providing maximum scalability. RackCDU ISAC™ typically has the RackCDU mounted in the server rack (In-RackCDU) along with the servers themselves and collects the heat from the servers without sharing any cooling liquid. In-RackCDU does not to take up any additional aisle space as it its mounted in the top 3U or 4U of the rack. Alternatively, ISAC has the option of using Vertical-RackCDU. The Vertical-RackCDU consists of a zero-U rack level CDU (Cooling Distribution Unit) mounted in a 10.5 inch rack extension to the back of the rack that includes space for 3 additional PDUs.
Features and Benefits
Captures nearly 100% of server heat
Enables thermal “room neutral” server racks
Sealed server airflow mitigates air quality concerns
No air is exchanged between servers and the data center
Provides data center cooling cost reductions exceeding 50%
Reduced data center OpEx and CapEx
Virtually eliminates the need for data center CRAC
Surveillance/alarm system supports DCIM via SNMP
Low pressure, redundant pumps for reliability
2.5x-5x increases in server density
How it Works
RackCDU ISAC Overview
Calculating the Benefits
Example - Increasing Server Density :
If a 1U server draws 1kW (1000W) total.
Data center is provisioned with CRAC supporting 8kW / rack.
Density is limited to 8 servers per rack.
All 1000W is removed by liquid.
CRAC units can be removed and CRAC piping infrastructure is converted to support ISAC racks.
Density now can expand to 42 servers per rack, a 425% increase.
Example - Data Center Power Savings:
If 1U server draws 500W and its CPUs use 60% of the wattage under load. A fully populated rack draws 21kW.
CRAC power draw to support 21kW is 7kW per rack. (Cooling PUE = 1.34)
100% of the thermal load is removed by liquid cooling.
CRAC infrastructure is converted to support ISAC.
Liquid cooling uses 3kW per rack.
$3,460 in net power savings per rack per year (@10 Cents/kWh)
Capital Cost Dynamics:
CRAC units and CRAC infrastructure is converted to support ISAC.